Evaluation of flat sheet membrane bioreactor efficiency for municipal wastewater treatment
Somayeh Fazeli1, Ali Fatehizadeh2, Amir Hesam Hassani1, Ali Torabian3, Mohammad Mehdi Amin2
1 School of Environment and Energy, Science and Research Branch, Islamic Azad University of Tehran, Tehran, Iran
2 Environment Research Center and Department of Environmental Health Engineering, School of Health, Isfahan University of Medical Sciences, Isfahan, Iran
3 Department of Civil-Environmental Engineering, University of Tehran, Tehran, Iran
|Date of Web Publication||15-May-2012|
Mohammad Mehdi Amin
Environment Research Center, Isfahan University of Medical Sciences, Hezar-Jerib Avenue, Isfahan
Source of Support: Isfahan Water and Wastwater Company., Conflict of Interest: None
Aim: In this paper, the feasibility of flat-sheet membrane bioreactor (FS-MBR) for municipal wastewater treatment was studied.
Materials and Methods: In this study, treatment of municipal wastewater in a submerged FS-MBR was investigated under different aeration time and flux. A bioreactor consist of microfiltration membrane (MF) and actual municipal wastewater as influent stream. The FS-MBR was operated during 161 days.
Results: The result showed that average removal efficiencies of chemical oxygen demand (COD), biological oxygen demand (BOD 5 ), total suspended solids (TSS) and volatile suspended solids (VSS) were obtained >90% and with variation of influent COD, BOD 5 , TSS and VSS, the removal efficiency no significantly change. The mixed liquor-suspended solids (MLSS) and mixed liquor volatile-suspended solids (MLVSS) concentration during experiment increases from low concentration to about 7.9 and 6.5 g/L, respectively. The average of PO4 3+ -P, total kjeldahl nitrogen (TKN), ammonia and fecal coliform (FC) removal efficiency during the operation period was 62, 98, 70% and 8 log, respectively.
Conclusion: It is concluded that FS-MBR can be used in the large scale municipal wastewater treatment plants to improve effluent quality due to high removal of COD, BOD 5 , TSS and VSS to meet effluent discharge standards.
Keywords: FS-MBR, microfiltration, municipal wastewater, submerged membrane
|How to cite this article:|
Fazeli S, Fatehizadeh A, Hassani AH, Torabian A, Amin MM. Evaluation of flat sheet membrane bioreactor efficiency for municipal wastewater treatment. Int J Env Health Eng 2012;1:19
|How to cite this URL:|
Fazeli S, Fatehizadeh A, Hassani AH, Torabian A, Amin MM. Evaluation of flat sheet membrane bioreactor efficiency for municipal wastewater treatment. Int J Env Health Eng [serial online] 2012 [cited 2020 Dec 1];1:19. Available from: https://www.ijehe.org/text.asp?2012/1/1/19/96008
| Introduction|| |
The available resources for potable water purpose are finite and application of wastewater provide the potential resources, so wastewater treatment and reuse is necessary. From 1970s, utilization of membrane separation processes have been developed and membrane unit used instead of the conventional secondary clarifiers in activated sludge treatment systems.  Membrane bioreactor (MBRs) can be broadly defined as systems integrating biological degradation of waste products with membrane filtration. They have proven quite effective in removing both organic and inorganic contaminants as well as biological entities from wastewater. 
The application of MBR process were progressed wastewater treatment due to reliability and simplicity. The first series of MBRs for municipal wastewater treatment in Europe were commissioned in 1998. The advantages offered by MBRs over conventional activated sludge process (ASP) include a small footprint, reduced sludge production, better control of biological activity, effluent that is free of bacteria and pathogens, smaller plant size, and higher organic-loading rates. ,,, In addition, MBRs have the advantage of allowing hydraulic retention time (HRT) and solids retention time (SRT) to be independent of each other and highly efficient nutrient removal. ,
The two main segment of a MBR including the activated sludge process and membrane separation process. In MBR, the microfiltration (MF) or ultrafiltration is used in order to separate MLSS from wastewater stearms microorganisms. , The reactor is operated similar to a conventional activated sludge process but no need to secondary clarification and tertiary steps like sand filtration. ,
The two main MBR configurations including either submerged membranes or external circulation (sidestream configuration).  The submerge configuration, the membrane unit are used in immersed system in bioreactor stream flowed out to in of membrane. The submerged MBRs are usually operated at low differential pressure and in comparison to sidestream type need to less pumping and operating cost and low cleaning and high aeration and investment costs. 
During last decade, MBR process exceedingly were used for treatment of domestic/municipal, industrial wastewater, potable and surface water and irrigation and processing water. , In previous study, the MBR was used for treating wastewaters with flat-sheet membrane , as well as with hallow fiber.  In these studies, organic material removal efficiency was obtained >95%. ,,
The aim of study was to investigate of flat-sheet membrane bioreactor (FS-MBR) efficiency in treatment of actual municipal wastewater.
| Materials and Methods|| |
This study was performed in a pilot scale FS-MBR system that was fed from a Isfahan South municipal wastewater plant (Iran) after primary sedimentation. The FS-MBR system consisted of a completely mixed aeration tank in which a bundle of flat sheet was immersed. The bioreactor was constructed of plexiglass with a working volume of 140 L and dimension of 130 × 23 × 65 cm. The membrane was made of polyethersulfone with a pore size of 0.2 μm and a filtration area of 0.5 m 2 . A schematic of FS-MBR is illustrated in [Figure 1].
|Figure 1: Exprimental set up of FS-MBR : 1) reserviour, 2) baffle plate, 3) PLC, 4) sensor, 5) bioreactor, 6) membrane module, 7) vacuum gauge, 8) suction pump, 9) flow meter, 10) permiate, 11) blower and 12) waste sludge.|
Click here to view
The influent manicipal wastewater was taken from the storage reservoir and fed to the bioreactor. To achieve an aerobic condition for the normal growth of activated sludge, an diffuser aerator was employed in bioreactor which also produced stirring within the reactor. A suction pump was used to extract the filtrate water from the membrane and initially, FS-MBR was operated under aerobic conditions and no sludge inoculation. The operating conditions are summarized in [Table 1].
The test methods were adapted from standard methods for the examination of water and wastewater. 
| Results|| |
The FS-MBR system removed chemical oxygen demand (COD), biological oxygen demand (BOD 5 ), total suspended solids (TSS), volatile suspended solids (VSS) at a high efficiency under all operating conditions, despite the fact that various of influent wastewater quality arrived to FS-MBR system. The results of the COD, BOD 5 , TSS, VSS removal efficiency during experiment are shown in [Figure 2],[Figure 3],[Figure 4] and [Figure 5].
|Figure 2: The variation of CODInf, CODEff and COD removal during operation|
Click here to view
|Figure 3: The profile of BODInf, BODEff and BOD5 removal during operation|
Click here to view
The [Table 2] is summarized the variation of influent and effluent concentration and removal efficiency of total kjeldahl nitrogen (TKN), ammonia, phosphorous and FC during operation of FS-MBR.
|Table 2: Effect of FS-MBR on nutrient and FC variation during experiment|
Click here to view
The variation of COD/BOD 5 ratio in influent wastewater and permeate are depicted in [Figure 6]. The average of COD/BOD 5 ratio in inlet waster and permeate was 2.1 ± 0.1 and 12.5 ± 4.1, respectively.
[Figure 7] shows the increasing of MLSS and MLVSS during the 110 days of FS-MBR operation. It can be seen that during 110 days, the MLSS and MLVSS increases from low concentration to about 7.9 and 6.5 g/L, respectively.
|Figure 7: Profile of comulative of surplus MLSS and MLVSS during study (Maximum sludge formation was obtained in 110th day of opration)|
Click here to view
[Figure 8] portrays the trends of the suction pressure (SP) increase during the 110 days operation of FS-MBR. It can be observed that during this period, the SP increases with time as the MLSS concentration in the bioreactor increases. The initial SP and the ultimate SP of the during this experiment was about 124 and 293 m Bar, respectively.
| Discussion|| |
The COD, BOD 5 , TSS, VSS removal performance of the FS-MBR system
The results showed that at the three HRTs employed, the COD, BOD5, TSS, VSS removal efficiency from the influent wastewater was consistently >91% [Figure 2],[Figure 3],[Figure 4] and [Figure 5]. Initially, COD and BOB 5 removal efficiency by FS-MBR was relatively low and this fact was due to insufficient biomass growth in system. The highest removal COD and BOD 5 efficiency was obtained at 48 and 153 day, with influent of 281.3 and 256.4 mg/L, respectively; that was >99%. The influent COD and BOD 5 was fluctuated from 228 and 112 to 740 and 295 mg/L, respectively; however, the concentration of COD and BOD 5 in filtrate was maintained at a low level.
This result is in accordance with Naghizadeh et al. and Grelot et al. that reported COD removal values higher than 95%, despite large fluctuations in influent conditions. ,
In all experiment, TSS and VSS concentration in filtrate is very low and the TSS and VSS removal efficiency of FS-MBR under all operating conditions was >98%. Because a MF membrane was used, the low levels of TSS and VSS was obtained. This results was confirmed by previous research. 
Variation of nutrient and FC removal
As it was expected, the removal efficiency of phosphorous in all operating conditions was not very high, because the system did not consist of an anerobic reactor. In MBR process that the sieving mechanisms was dominate, typically, particulate phosphorous eliminated. The average of PO 4 3− -P removal efficiency of the FS-MBR during the operation period was 62.1 ± 4.7%. These results were in agreement with Chae and shin. 
The nitrate was present in feed wastewater at low concentration (0.01 mg/L), it was produced as a result of nitrification of NH 4 -N during the oxic (aerobic) phase (8.9 mg/L) and converted to N 2 during the anoxic phase. Therefore, nitrate removal efficiency is also an important parameter for nutrient removal operations.
In this study, the ammonia removal efficiency was very high (>98%) because in aerobic condition, the ammonia was converted to nitrate during nitrification cycle. The result are in line to Blstakova et al. 
The average of FC removal in FS-MBR was 8 log and related to this fact that, the size of FC is higher than membrane porous. Grelot et al. mentioned similar results and reported that by application of FS-MBR filtration, total coliforms removal can achieved to 7.2 log. 
Effect of HRT on FS-MBR performance
The effect of HRT was minimal on organic removal and COD and BOD5 removal by FS-MBR and was found to be greater than 91%, even with a short HRT. The result of this study are in line to Chang et al.  COD and BOD 5 removal in the bioreactor decreased slightly from 97 and 99% to 95 and 98% with fluctuation HRT from 20 to 12h, respectively.
In general, a short HRT can induce a large OLR. Thus, HRT is expected to be an important operating parameter in MBR systems, correlated not only to the treatment efficiency of the MBR system itself  but also to the characteristics of the biomass in the activated sludge system. ,
Surplus sludge production during operation
During operation of FS-MBR, the MLSS and MLVSS content in the reactor continued to rise from low concentration to almost 7.9 and 6.5 g/L [Figure 7]. The results are well consistent with the studies conducted by Khongnakorn et al. and Wang et al. , Initially, the MLVSS/MLSS ratio was 0.78 and then gradual increase in the ratio of MLVSS/MLSS to 0.82 after 110 days of operation. The augment in the ratio of MLVSS/MLSS indicates that biological activity of the reactor may have improved over the time. The previous study reported that the variation in the MLSS content in the reactor did not exert any discernible influence on the overall biological performance of the MBR system.  But, Ren et al. reported opposite observation and mentioned that COD removal increased with increase of MLSS. 
At equivalent sludge residence time, the sludge production of the MBR is less than that commonly reported in the literature for conventional processes. , The low sludge production rate, or even complete stagnation of MLSS for MBRs, has been reported earlier,  and explained by low food to microorganism ratio, which lead to competition among the microorganisms and resulted in a reduction of sludge production. To maintain membrane permeability, the SMBR process is limited to maximum mixed liquor suspended solids (MLSS) concentrations of 10 - 20 g/L. 
The variations of suction pressure
The characterization of fouling during the operation of FS-MBR in the present study was performed through monitoring of suction pressure (SP) [Figure 8]. It can be observed that during operation period, the SP increases with time as the MLSS concentration in the bioreactor increases. Liu et al. and Hong et al. reported similar observation. , It was reported that membrane fouling could result in a reduction of permeate flux or an increase in SP (or TMP) depending on the operation mode used.  The SP, which indicates the extent of membrane fouling, was monitored at regular intervals. FS-MBR is usually operated for high concentration of sludge biomass, which could lead to membrane fouling that could decrease the flux and increase the SP.
Fouling most commonly takes place external to the membrane, forming a dynamic layer at the membrane surface. As most membrane processes operate in the cross flow mode, fouling through the formation of such a dynamic layer might be expected to reach equilibrium once the adhesive forces between the layer and the membrane substrate are balanced by the shear forces at the layer-solution interface. In practice, equilibrium is not always attained, indicating some component of the overall hydraulic resistance to be time dependent.  It was understood that the formation and maturation of the biofilm on the suspended carriers resulted in much less accumulation of foulants on the membrane surface.
It is concluded that FS-MBR can be used in the large scale municipal wastewater treatment plants to improve effluent quality due to high removal of COD, BOD 5 , TSS and VSS to meet effluent discharge standards.
| Acknowledgment|| |
This work was supported by through a grant provided by Isfahan Water and Wastwater Company. The authors are thankful to the staff of Isfahan South WWTP.
| References|| |
|1.||Grelot A, Tazi-Pain A, Weinrich L, Lesjean B, Grasmick A. Evaluation of a novel flat sheet MBR filtration system. Desalination 2009;236:111-9. |
|2.||Cicek N, Winnen H, Suidan MT, Wrenn BE, Urbain V, Manem J. Effectiveness of the membrane bioreactor in the biodegradation of high molecular weight compounds. Water Res 1998;32:1553-63. |
|3.||Hai FI, Yamamoto K, Nakajima F, Fukushi K. Application of a GAC-coated hollow fiber module to couple enzymatic degradation of dye on membrane to whole cell biodegradation within a membrane bioreactor. J Membr Sci 2012;389:67-75. |
|4.||Gander M, Jefferson B, Judd S. Aerobic MBRs for domestic wastewater treatment: A review with cost considerations. Sep Purif Technol 2000;18:119-30. |
|5.||Monclus H, Buttiglieri G, Ferrero G, Rodriguez-Roda I, Comas J. Knowledge-based control module for start-up of flat sheet MBRs. Bioresour Technol 2012;106:50-4. |
|6.||Melin T, Jefferson B, Bixio D, Thoeye C, De Wilde W, De Koning J, et al. Membrane bioreactor technology for wastewater treatment and reuse. Desalination 2006;187:271-82. |
|7.||Naghizadeh A, Mahvi AH, Vaezi F, Naddafi K. Evaluation of hollow fiber membrane bioreactor efficiency for municipal wastewater treatment. Iran J Environ Health Sci Eng 2008;5:257-68. |
|8.||Till S. Membrane bioreactors: Wastewater treatment applications to achieve high quality effluent. 64th annual water industry engineers and operator's conference. 2001:57-63. |
|9.||Achilli A, Cath TY, Marchand EA, Childress AE. The forward osmosis membrane bioreactor: A low fouling alternative to MBR processes. Desalination 2009;239:10-21. |
|10.||Wang Z, Wu Z, Mai S, Yang C, Wang X, An Y, et al. Research and applications of membrane bioreactors in China: Progress and prospect. Sep Purif Technol 2008;62:249-63. |
|11.||Shim JK, Yoo IK, Lee YM. Design and operation considerations for wastewater treatment using a flat submerged membrane bioreactor. Process Biochem 2002;38:279-85. |
|12.||APHA. Standard methods for examination of water and wastewater. 21 th edition. Washington DC, USA: American Public Health Association Publication; 2005. |
|13.||Naghizadeh A, Mahvi AH, Mesdaghinia AR, Alimohammadi M. Application of MBR Technology in Municipal Wastewater Treatment. Arab J Sci Eng 2011;36:3-10. |
|14.||Chae SR, Shin HS. Characteristics of simultaneous organic and nutrient removal in a pilot-scale vertical submerged membrane bioreactor (VSMBR) treating municipal wastewater at various temperatures. Process Biochem 2007;42:193-8. |
|15.||Blstakova A, Bodik I, Dancova L, Jakubcov Z. Domestic wastewater treatment with membrane filtration - two years experience. Desalination 2009;240:160-9. |
|16.||Chang JS, Chang CY, Chen AC, Erdei L, Vigneswaran S. Long-term operation of submerged membrane bioreactor for the treatment of high strength acrylonitrile-butadiene-styrene (ABS) wastewater: Effect of hydraulic retention time. Desalination 2006;191:45-51. |
|17.||Ren N, Chen Z, Wang A, Hu D. Removal of organic pollutants and analysis of MLSS-COD removal relationship at different HRTs in a submerged membrane bioreactor. Int Biodeterior Biodegradation 2005;55:279-84. |
|18.||Yoon SH, Kim HS, Yeom IT. The optimum operational condition of membrane bioreactor (MBR): Cost estimation of aeration and sludge treatment. Water Res 2004;38:37-46. |
|19.||Cho J, Song KG, Lee SH, Ahn KH. Sequencing anoxic/anaerobic membrane bioreactor (SAM) pilot plant for advanced wastewater treatment. Desalination 2005;178:219-25. |
|20.||Wang Z, Wu Z, Hua J, Wang X, Du X, Hua H. Application of flat-sheet membrane to thickening and digestion of waste activated sludge (WAS). J Hazard Mater 2008;15:535-42. |
|21.||Khongnakorn W, Wisniewski C, Pottier L, Vachoud L. Physical properties of activated sludge in a submerged membrane bioreactor and relation with membrane fouling. Sep Purif Technol 2007;55:125-31. |
|22.||Tadkaew N, Sivakumar M, Khan SJ, Mc Donald JA, Nghiem LD. Effect of mixed liquor pH on the removal of trace organic contaminants in a membrane bioreactor. Bioresour Technol 2010;101:1494-500. |
|23.||Chaize S, Huyard A. Membrane bioreactor on domestic wastewater treatment sludge production and modelling approach. Water Sci Technol 1991;23:1591-600. |
|24.||Bouhablla EH, Aim RB, Buisson H. Microfiltration of activated sludge using submerged membrane with air bubbling (application to wastewater treatment. Desalination 1998;118:315-22. |
|25.||Rosenberger S, Kruger U, Witzig R, Manz W, Szewzyk U, Kraume M. Performance of a bioreactor with submerged membranes for aerobic treatment of municipal wastewater. Water Res 2002;36:413-20. |
|26.||Trussell RS, Adham S, Trussell RR. Process limits of municipal wastewater treatment with the submerged membrane bioreactor. J Environ Eng 2005;131:410-417. |
|27.||Hong S, Aryal R, Vigneswaran S, Johir MA, Kandasamy J. Influence of hydraulic retention time on the nature of foulant organics in a high rate membrane bioreactor. Desalination 2012;287:116-22. |
|28.||Liu Q, Wang XC, Liu Y, Yuan H, Du Y. Performance of a hybrid membrane bioreactor in municipal wastewater treatment. Desalination 2010;258:143-7. |
|29.||Meng F, Chae SR, Drews AJ, Kraume M, Shin HS, Yang F. Recent advances in membrane bioreactors (MBRs): Membrane fouling and membrane material. Water Res 2009;43:1489-512. |
[Figure 1], [Figure 2], [Figure 3], [Figure 4], [Figure 5], [Figure 6], [Figure 7], [Figure 8]
[Table 1], [Table 2]